电话：151 6888 2846
Compared with the traditional roller shutter door, the electric roller shutter door reduces the tedious process of unlocking and sliding the door, and is very suitable for modern people. There are many precautions in the installation, use and maintenance of electric roller shutter doors, which many people often know little about. The Jinan roller shutter door editor will introduce these precautions for you, so as to provide you with reference when you need them.
Reliable fire protection facilities shall be provided at the upper end of the installation position of the electric roller shutter door. When the lower end of the drum of the roller shutter door is used as a packing box or ceiling, a detachable movable cover plate shall be provided, and 500 mm shall be reserved at the lower end of the side of the electric roller shutter door × 500mm removable manhole for easy maintenance.
The opening and closing direction of all electrically controlled roller shutter doors shall be the same as that indicated by the switch box. In particular, when the power supply is newly connected for trial run or the external input power is used to change the phase line, the manual device shall be used first to place the door shutter at the position of 1 / 2 of the door opening height. After the power supply is connected, the roller shutter shall be opened and closed for trial operation until it is attached with the indication. Otherwise, the stopper will be damaged, causing the roller shutter to reverse roll or flush, causing losses.
During the operation of the electric roller shutter door, the operator must stand at the position where the operation state of the roller shutter door can be seen, otherwise it is easy to be damaged by accident.
The electric roller shutter door curtain and the roller shutter machine shall not be in contact with acid and alkaline solutions to prevent corrosion of the door curtain surface.
The rolling door machine shall be regularly inspected (at least twice a year) during operation, sliding, transmission and other parts, and timely refueled as required to ensure the normal use of the rolling door.
In the process of opening and closing, the electric roller shutter door shall have the function of following the position, and shall not stop and continue to slide. If the sliding distance is greater than 50mm, the control electric appliance of the roller shutter door and the roller shutter mechanism shall be carefully inspected and repaired immediately until the operation is normal.
The electric roller shutter door curtain and rust prone parts shall be subject to regular anti-corrosion, paint and maintenance treatment. It is prohibited to impact the door surface with heavy objects and hard objects.
In case of large shaking or abnormal sound during the operation of the electric roller shutter door, stop the machine for inspection to eliminate the sundries that hinder the normal opening and closing of the door shutter.
The upper limit position of the bottom beam seat of the electric roller shutter door must be kept at a distance of more than 200mm from the lower end of the bearing frame to ensure that there is no rush when the brake stops.
Through the above introduction, we have generally understood the precautions during the installation, use and maintenance of the electric roller shutter door. We can see from the above that during the installation of the electric roller shutter door, attention should be paid to the tight connection of all parts, and repeated inspection should be conducted before putting it into use to avoid any problems in the process of use. For more information, please visit our website http://www.jnzxmy.com Consult and understand.